Scheduled maintenance is currently in progress. We will provide updates as necessary.
Posted 10 months ago. Mar 17, 2018 - 20:00 GMT
Global Switch will be carrying out essential emergency maintenance to disconnect the output signal cables from the breaker temperature monitoring unit, preventing any spurious trip signal to the Main Incomer LV ACB. This sensor has been identified as a possible contributor to the recent interruption to power experienced on the 10th March 2018. We are not expecting any service impact during this work, however due to the nature of the maintenance, we are announcing an "AT RISK" window.
The works will only proceed if Global Switch are happy that there are no identifiable risks that could impact the supply to PSS/10A
Location: Global Switch 2, 10th Floor, Racks in rows "A", "B", "C"
Start: 17/03/2018 - 20:00 GMT (UTC + 0)
End: 17/03/2018 - 20:30 GMT (UTC + 0)
Affected Services: Power
Reason: Risk Mitigation
Rollback plan: Not Applicable
If you have any questions regarding this maintenance, please don't hesitate to contact us via the usual methods.